The magnetic micro gear pump is well known to all. It is widely used in petroleum, chemical, pharmaceutical, electroplating, environmental protection, water treatment, film and television printing, national defense and other departments for pumping flammable and explosive products because of its fully sealed, leak-free and corrosion-resistant characteristics. Toxic and precious liquids are ideal pumps for creating leak-free, pollution-free civilized workshops and cultural factories. Today, we mainly introduce the following considerations in the installation process of magnetic micro-gear pump: 1、将机组放在基础上，在底板和基础之间放成对楔垫，通过调整楔垫，找正泵的水平。调好后，拧紧地脚螺栓。
1. Put the unit on the base and set a pair of wedge cushions between the base plate and the base. By adjusting the wedge cushion, the pump level can be corrected. After adjustment, tighten the anchor bolt.
2. Before installation, magnetic pumps and motors should be inspected. All parts should be intact, and there should be no impurities in the magnetic pumps.
3. Make the concrete foundation according to the size of the foundation, and bury the foot bolts.
4. The suction and vomiting pipelines of the magnetic pump should have brackets, which can not be supported by the magnetic pump. The diameter of the inlet and outlet pipe should be unified with the diameter of the pump inlet and outlet.
5. After installation, the magnetic pump coupling is finally rotated by hand to check whether there is any rubbing phenomenon. When the rotation is easy and even, the installation is completed.
6. It is strictly forbidden to extract medium with granules and easy crystallization from magnetic pumps. It is not allowed to operate continuously when the discharge outlet is closed. The minimum flow rate should be maintained.
7、为防止杂物进入磁力泵内，在进口处应设过滤器，过滤面积应大于管路截面积的 3 ～ 4 倍。
7. In order to prevent impurities from entering the magnetic pump, filters should be installed at the inlet, and the filter area should be 3-4 times larger than the cross-section area of the pipeline.
8. When the medium viscosity is too high, the performance and power of the magnetic pump will change. Please follow the instructions for details.
9. The installation height of the magnetic pump must be guaranteed to meet the cavitation allowance of the pump, and the loss of pipeline and medium temperature should be taken into account.
标签:   环氧地坪 地坪 环氧地坪漆 环氧地坪施工 微型齿轮泵